Welcome to Aerotech Energy PVT. Ltd
Noise is undesirable or unwanted sound. With better understanding of the effects of environment on the inmates of the dwellings and factory workers, noise has become an important subject in the design, installation, and operation of the fans.
In a well-balanced properly installed fan, the mechanical noise originating from bearing and vibration of various parts is not as prominent as the aerodynamically generated noise. The latter is due to the various flow phenomena occurring within the fan.
The main causes of aerodynamically generated noise are:
Some methods of reducing fan noise are:
Fan Laws for Sound
Dimension analysis indicate that the sound power ratio SWR = SW/W of geometrically similar series of fans should be dependent only on Mach number, Ma = V/Va, (ratio of a typical fan velocity to the velocity of sound) and Reynolds number, Re = DVp m which is the ratio of the dynamic to viscous forces involved, SWR = constant x (Ma)xx (Re)y
Taking the rotational speed N, diameter D, and output power W of the impeller as the typical quantities:
W µ N3D5 Maµ ND Re µ ND2
Therefore SW = constant x N3 + x + y D5 + x +2y
Acoustical theory, considering only the Mach number effect, yields the following relations for the source types mentioned
Monopole Source x = 1 so that SW varies as V4
Dipole Source x = 3 so that SW varies as V6
Quadrupole Source x = 3 so that SW varies as V8
Fan noise is principally dipole in origin and, for the simplest cases of boundary layer separation, there is reason to believe that the Reynolds number exponents y should be about - 0.4, leading to:
SW = constant x N5.6 D7.2
Axial fans seems to follow this relationship quite closely (e.g. N5.5 D7.5), but other type may well introduce more complex generation mechanism. For example, centrifugal fans are usually considered to follow the law:
SW = constant x N5 D7
Geometrical similarity as its affects Reynolds number is not well maintained in practice from size to size (thickness, clearances, even number of blades). It is wise to keep the index of D2 greater than the experimental index of N and to treat small changes with size as a scale effect on the constant. The influence of atmospheric conditions is small -generally within 1 dB.
We introduce ourselvesas one of the renowned manufacturers of Energy Efficient FRP Hollow Axial Flow Fans Assemblies.
We regularly supplying our products to various OEM Companies for their Turnkey Projects in India and Abroad.